﻿ Case History 191: The weakest link. - March 2024 - Michael Brown Control Engineering - SA Instrumentation & Control

#### Case History 191: The weakest link.

March 2024 Valves, Actuators & Pump Control

Many years ago there was a popular quiz programme on TV, hosted by Anne Robinson, where the players voted in each round to determine who was the weakest link. Which is the weakest link in a control loop? The answer, without any doubt is that, in most cases, the final control element is the weakest link.

As mentioned in the previous article, the elements of the control loop consist of the process itself, the transmitter, the controller, and then the final control element. There are many types of final control elements, ranging from simple resistive heating elements through to more sophisticated devices such as variable speed pumps; but, in most plants the final element consists of a valve, an actuator, a positioner and an I/P current to pneumatic converter. Pneumatically-actuated valves have been in use for well over a century. They are simple and reliable, but are not very sophisticated or accurate devices. This is one of the main reasons why a positioner should always be used with this type of actuator.

In general, about 80% of all problems are due to faults in the final control element. The problem lies in the fact that valves are mainly mechanical devices, and must face all sorts of possible challenges, such as high and possibly varying pressure, friction, abrasion, corrosion, loose linkages and hysteresis, to name a few.

What is the actual purpose of the final control element? Simply put, its function is to translate a 0-100% signal from the controller’s output into an actual physical happening. The controller compares the actual value of the process variable (PV) with the SP setpoint (SP), and performs a relatively uncomplicated mathematical calculation that outputs a signal (called, by us, the process demand − PD) that demands that the final control element should go to a position where the actual desired quantity of process fluid or substance is fed into the process in order for the PV to reach the SP.

As an example, say a heat exchanger is heating a process fluid by injecting steam into the other side of the exchanger, and if the PD is at 55%, then the final control element is required to feed exactly 55% of the total range of the steam flow into the exchanger. The quicker and more accurately the final control element complies with that demand, the better the control, with the least variance.

When a control valve is really bad, the control can get to the point where it just cannot work, and sometimes it becomes absolutely necessary to get the valve fixed, or if this is not possible, to have it replaced. In spite of this, I have often found people still believing that a ‘miracle’ tune will sort out the problem. I have come across cases where they spend literally days and even weeks trying different tuning to get it to work, all to no avail.

The example given in this article is of a combustion air flow in a furnace in a petrochemical refinery. It was vital that the furnace temperature should be kept constant at SP, as quite a few downstream processes were dependent on it. However the temperature was usually not at its SP. Investigation revealed that the problem was related to the performance of the combustion air flow, which did not respond quickly enough to deal with load disturbances on the temperature process. This was a rather unusual problem, as airflow is such a fast process compared with temperature, and even rather poor flow control will not usually affect the temperature too much.

Figure 1 shows a recording of an As Found closed loop test on the flow loop, where step changes were made on the SP with the original tuning parameters in the controller to judge the control response. It was found that the tuning was abysmally slow, typically taking over 25 minutes for the process to respond to a 3% change in SP. On discussing this with the C&I; staff, I was told that they couldn’t get it to work faster as it tended to go into what they described as ‘crazy cycling’ as soon as they tried to speed it up. Normally, a flow loop should fully respond to a small SP step like that in a few seconds.

A second interesting thing seen in the test was that on the second upwards step of SP, the PD had to move much more than it did on the first step, even though the two steps were of equal size. This could have indicated several problems, including non-linear installed valve characteristics. However, on the first reverse step downwards, the PD had to move much less. This was a little puzzling, and may also have indicated that the valve was very sticky on opening.

An open loop test was then performed on the flow loop, making step changes on the PD, and this shown in Figure 2. This is quite interesting as it shows that there were several serious problems with the valve. These were:

1. When the valve reversed from the closing direction, there were sometimes huge overshoots when it moved in the opening direction again. On some occasions, the valve then recovered and moved slowly back down to the correct position. However, it sometimes did not do this and stuck in the overshoot position.

2. There were some occasions where the valve also had big overshoots on other opening steps.

3. These occurrences made the valve effectively non-repeatable, and really inhibited good control.

4. There did appear to be some non-linearity in the valve installed characteristics. However, of more importance, and very seriously, the flow started saturating above 63%. A subsequent test (not shown here) showed that the maximum flow that could be obtained with the valve fully open was 76%. Under normal operating load conditions the flow SP was just over 70%. Good control in this saturated region was almost impossible. As mentioned above, the closed loop test in Figure 1 shows clearly how much the PD had to move on the second upwards SP step to try and get the PV to SP. The reason for this saturation was most likely insufficient upstream pressure in the air stream.

These findings show that good automatic control of the flow will not be possible if the saturation problem is not sorted out, and if the valve is not fixed or replaced to follow the PD properly. Once again it can be seen how very important it is to first analyse a loop thoroughly to determine if there are any problems before even thinking of tuning the controller.

Michael Brown.

Michael Brown is a specialist in control loop optimisation, with many years of experience in process control instrumentation. His main activities are consulting and teaching practical control loop analysis and optimisation. He now presents courses and performs optimisation over the internet. His work has taken him to plants all over South Africa and also to other countries. He can be contacted at: Michael Brown Control Engineering CC, +27 82 440 7790.

Credit(s)

 Email: [email protected] www: www.controlloop.co.za Articles: More information and articles about Michael Brown Control Engineering

Compact valve position indicator
Emerson Automation Solutions Valves, Actuators & Pump Control
Emerson’s new TopWorx DVR Switchbox is an entry-level addition to the DV Series of valve position indicators. It combines a durable resin enclosure, compact size, and a patented cam design that provides a reliable valve position feedback for water and wastewater systems, food and beverage production lines, and industrial utilities.

Selection of two-port valves: an open and shut case
SMC Corporation South Africa Valves, Actuators & Pump Control
Little consideration is generally given to two-port valves because they are often perceived as simple devices that only open and close to control downstream fluid supply. Although this is mechanically true, choosing the optimal two-port valve for your application can make a big difference, saving space, weight and energy consumption.

Dependable pumping for dewatering in hard rock mining areas
Valves, Actuators & Pump Control
Becker Mining’s Pumpor Vertical Spindle (PVS) pumps are hard at work on many mines throughout Africa, with many units installed recently in the Carletonville area, West of Johannesburg.

Efficient, affordable solution for electrohydraulic pumps
Parker Hannifin - Sales Company South Africa Valves, Actuators & Pump Control
In the world of construction a revolution is changing the status quo, the electrification of small and efficient construction machinery.

Redefining Industrial Automation with the new Festo Valve Terminal
Festo South Africa Valves, Actuators & Pump Control
Festo recently introduced its latest innovation in the form of the Valve Terminal VTUX. This invention marks the beginning of a new era in valve terminals, with its features making it an impressive solution for the future.

Loop signature 22: How cyclical disturbances affect a control loop
Michael Brown Control Engineering Editor's Choice
When tuning noisy loops, we recommend in our courses that one should eliminate the noise by editing it out, so the tuning will be done only on the true process response, free of any noise. The controller is controlling the process, and is not controlling the noise.

New pilot-operated relief valve
Emerson Automation Solutions Valves, Actuators & Pump Control
Emerson has introduced a pilot-operated relief valve for installation on pressurised bullet tanks used to store liquid propane and anhydrous ammonia. This type of pressure relief valve is typically installed on tanks fabricated by OEMs for end users, engineering firms, or contractor customers.

Pulse valves for dust collection
Emerson Automation Solutions Valves, Actuators & Pump Control
In process manufacturing, especially hard mineral mining, dust particles are unavoidable. If this pervasive dust is not effectively removed, it can accumulate throughout mines, plants and other facilities, becoming hazardous to workers and equipment.

High-flow solenoid valve
Emerson Automation Solutions Valves, Actuators & Pump Control
Emerson has introduced the new ASCO Series 327C solenoid valve, which features a direct-acting, high-flow design that provides superior flow-to-power ratio. It permits high flows at minimum power levels, making it ideal for use in power plants, refineries, and chemical processing facilities.

Selection of two-port valves: an open and shut case
SMC Corporation South Africa Valves, Actuators & Pump Control
Little consideration is generally given to two-port valves because they are often perceived as simple devices that only open and close to control downstream fluid supply. Although this is mechanically true, choosing the optimal two-port valve for your application can make a big difference, saving space, weight and energy consumption.