﻿ Reliably determine actual fieldbus availability - June 2014 - Pepperl+Fuchs - SA Instrumentation & Control

#### Reliably determine actual fieldbus availability

June 2014 Fieldbus & Industrial Networking

Communication via fieldbus is highly valued in process automation due to its reliability. Like any installation technology, however, it is not exempt from faults and failures. But what is the actual risk of failure and what availability can be realistically assumed? Calculations often provide an unsatisfactory reflection of the real situation. This results not only in incorrect assumptions, but often in protective measures that are expensive and barely effective.

In practice, to what degree does availability affect whether a fieldbus installation is commissioned? You need to understand what can cause problems and how best to protect against them, so that you can take preventive measures and ensure increased fieldbus availability. However, availability calculations are based on descriptions, assumptions, and observations from the theory of probabilities. Here at Pepperl+Fuchs, we have discovered from many years of interaction with users that these calculations are based on assumptions that are sometimes unrealistic, and sometimes just plain wrong. Of course, the results of such calculations do not really reflect reality.

What do we mean by actual availability?

The International Electrical Vocabulary (IEV) has 47 different definitions of the term availability and, accordingly, different ways of calculating it. Stationary availability is usually called availability (A) for short. It is defined as the mean value of current availability in a time interval. The mean time to failure, called MTTF, and the mean down time, called MDT, can be used for a simplified calculation of the stationary availability, provided these values are constant. In this case, the following formula is used for the calculation:

Often, the inverse of the Lambda failure rate for a product or series of products is mistakenly used to calculate the MTTF, such as for a fieldbus segment. But this procedure reflects only the random failure of the component(s). This means that important systematic criteria are not being taken into account. In practice, these criteria play a crucial role in availability: When environmental influences as well as the mode of operation and its effect are not accounted for in the calculation, a significant discrepancy arises between the mathematical theory and the effect in practice when it comes to process automation. However, a brief glance at alarm and failure statistics makes it very clear that it is precisely the effects of the mode of operation and environmental conditions that are responsible for faults much more frequently than random events that cause component failure.

An example shows the difference

The extent to which this type of one-dimensional view can distort reality when calculating availability is shown by a simple example: If a person in his role as employee is used instead of the process system, the result is an MTTF of 1401 years or 72 800 weeks according to the above-mentioned procedure. But this value takes into account only the ‘total failure’ i.e., possible death of an employee, which certainly does not accurately reflect the employee’s actual availability in his professional life. If you further assume that a replacement is found for a failed employee after six weeks (=MDT), the availability is calculated as:

Of course, important aspects of everyday working life remain unaccounted for. Much more frequent causes of absence from the workplace are vacation, illness, doctor’s appointments, or business trips, which can occur several times a year. If you assume that a failure of on average two weeks occurs twice a year for these reasons, the availability is calculated as:

Reduction of failure risks

Finding the right method of calculating availability is just the first basic step. Once you have calculated reliable figures for the actual availability of a plant, it follows that you must take measures to reduce the failure rates effectively and thus increase availability. Systematically, there are four methods to protect against a component or part of a system failing and thus positively influence the MTTF.

First: Preventive measures and procedural instructions must be given. The correct and protective handling of technology is often enough to help reduce failures significantly.

Second: The predictive, automated handling of faults. With this method, techniques and components are used that have been specially developed to detect and isolate typical faults in a targeted and proactive manner, before they can spread. The impact of the fault remains limited to a deactivated device, while the plant itself remains in operation. For example, if a measuring device connection is deactivated in the case of a short circuit, but the fieldbus segment remains unaffected, because the failure of an individual measuring part is tolerable.

Third: The detection of faults through diagnostics. With this method, discrepancies between the actual status and the best possible status are detected through monitoring and reported to the control room. Before this can have a negative impact on the overall function, proactive intervention can be taken. For example, if you measure a change in the frequency of filling level sensors using a tuning fork, this indicates that the sensor has become jammed. The problem can then be corrected.

Fourth: Redundancy. This protects against failures whose causes have to be investigated in the device itself. Redundancy is indispensable if these faults cannot be avoided in any other way, but must absolutely be controlled to ensure safety or plant availability. This is the case for power supplies and control technology boards or for field devices where the measuring circuit is required to have a very high level of availability.

For more information contact Mark Bracco, Pepperl+Fuchs, +27 (0)87 985 0797, mbracco@za.pepperl-fuchs.com, www.pepperl-fuchs.co.za

Credit(s)

 Tel: +27 87 985 0797 Fax: 086 756 8741 Email: info@za.pepperl-fuchs.com www: www.pepperl-fuchs.co.za Articles: More information and articles about Pepperl+Fuchs

The safety over OPC UA concept
June 2019 , Fieldbus & Industrial Networking
Another problem with existing safety protocols is the lack of a concept for dynamically establishing and terminating connections. The current state of technology requires that early during the project ...

Interference-free transmission with the Ethernet media converter
June 2019, Phoenix Contact , Fieldbus & Industrial Networking
The new FL MC EF 660 SCRJ media converter from Phoenix Contact enables the connection of cost-effective polymer and HCS/PCF fibre technology. The optical transmission of data via fibre optics is free ...

Rail-mount fibre optic distributor for network expansion
June 2019, Webb Industries , Fieldbus & Industrial Networking
Jasco’s Webb Industries has introduced Telegärtner’s new, modular rail-mount fibre optic distributor. The all-new STX distributor can be extended according to actual needs. The stackable modules allow ...

Powerful new remote I/Os
Africa Automation Fair 2019 Preview, Vision Automation , Fieldbus & Industrial Networking
UniStream Remote I/Os are a powerful addition to the UniStream series. The line comprises an Ethernet-based remote I/O adaptor and a broad range of remote I/O modules, such as analog and digital I/Os ...

Mobility for Industry 4.0 ­challenges
Africa Automation Fair 2019 Preview, Pepperl+Fuchs , Industrial Wireless
The Tab-Ex 02 series of tablets from Pepperl+Fuchs has innovative features that make Industry 4.0/IIoT applications easy to implement.    The DZ1 version ecom has a range of applications that are unique ...

Combine process and motion control with Profinet networking
Africa Automation Fair 2019 Preview, Varispeed (Div of Hudaco Trading) , Fieldbus & Industrial Networking
Yaskawa’s MICRO CPU provides high performance and channel density, with prepared PLC and HMI/scada motion software libraries for Yaskawa servos and VSDs. At 0,02 μS per instruction and direct execution ...

Africa Automation Fair 2019 Preview, Pepperl+Fuchs , Sensors & Transducers
Pepperl+Fuchs has on show a range of IO-Link infrastructure components. As a globally established communication standard that is system- and fieldbus-independent, IO-Link offers many advantages. The universal ...

May 2019, Turck Banner , Fieldbus & Industrial Networking
Turck has expanded its extensive IO-Link portfolio with new Class A and Class B I/O hubs with protection to IP67, and HF RFID read/write heads with threaded barrel design. Thanks to SIDI, the Simple IO-Link ...

All-in-one mobile network analyser
Africa Automation Fair 2019 Preview, Industrial Data Xchange (IDX) , Fieldbus & Industrial Networking
On show at Stand D20, the PROCENTEC Mercury from Industrial Data Xchange is an all-in-one mobile analyser that gives the user the ability to troubleshoot, maintain and monitor both Profibus and industrial ...

Next generation Layer 3 Ethernet backbone
Africa Automation Fair 2019 Preview, IAC - Industrial Automation & Control , Fieldbus & Industrial Networking
The Hirschmann DRAGON MACH4500 Layer 3 Ethernet backbone is ideal for applications that require high bandwidths and reliable data transfer. This flexible, future-oriented solution supports redundant internal ...