﻿ How to calculate an intrinsically safe loop approval - September 2017 - Extech Safety Systems - SA Instrumentation & Control

#### How to calculate an intrinsically safe loop approval

September 2017 IS & Ex

We all know what can happen if the correct techniques are not used when interfacing into the hazardous area. Using intrinsic safety (Ex i based on IEC/SANS 60079-11; IEC/SANS 60079-25), the energy in the hazardous area is limited to below the ignition energy of the gas present, thereby preventing explosions.

For an explosion, all three of gas/dust, oxygen and source of ignition (spark or heat) need to be present. Intrinsic safety works on the principle of removing the source of ignition. This can be achieved by using a Zener barrier or galvanic isolator.

Zener barrier

A Zener barrier is a simple device where the voltage is limited by a Zener diode and the current by a resistor. A fuse is present to protect the Zener diode as shown in Figure 1. The key to safety is the intrinsically safe earth. Without it, there is no protection. If the input voltage increases above Zener diode voltage, the Zener conducts and the fuse blows, after which the Zener barrier needs to be replaced. In addition, the barrier has a volt drop across it under normal operating conditions, so careful calculation must be done to ensure that there is sufficient voltage at the field device. [Note: using Zener barriers without an IS earth is not safe.]

Figure 1.

Galvanic isolator

A galvanic isolator is an active device that energy limits without the dependence on the IS earth for safety as shown in Figure 2. It also has the advantage of supplying higher voltage at the hazardous area terminals and allowing longer cable lengths. Isolators have local LED indication and most 4-20 mA isolators transfer Hart communications through the optical isolation.

Figure 2.

Figure 3 defines Ex i for the various classifications of hazardous zones.

Figure 3.

Figure 4 shows that the barrier/isolator has [Ex ia] IIC; the square brackets indicate that the device (mounted in a safe area) can have connections to the hazardous area, in this case Ex ia i.e. zone 0 – IIC is the gas group. This transmitter has Ex ia IIC T4, which means it can be located in zone 0 in gas group IIC – T4 is the maximum surface temperature of the device (135°C).

Figure 4.

The barrier/isolator has maximum output parameters for voltage, current and power (Uo, Io and Po). These are maximum output values under fault conditions (known as safety description or entity parameters). The field device has maximum input parameters (Ui, Ii and Pi), which are the maximum values that can be applied under fault conditions and still be safe. [Note: for a safe loop all three input parameters must be greater than or equal to the corresponding output parameters.

To complete the system loop approval, the electrical energy stored in the cabling needs to be considered. Table A.2 in IEC/SANS 60079-11 lists the maximum cable capacitance against output voltage. In the example shown the maximum electrical stored energy that can be connected to the hazardous area terminals equates to Co = 83 nF and Lo = 4,2 mH. The transmitter has internal capacitance and inductance, so maximum cable capacitance Cc = Co-Ci and maximum inductance Lc = Lo-Li. The cable specification typically gives pF/m and μH/m allowing a calculation of maximum cable length

Based on this assessment, a system certificate or loop approval can be documented. [Note: inserting a barrier or isolator with a non-certified field device is not safe.] Some field devices (see Figure 5) like thermocouples are defined as Simple Apparatus.

Figure 5.

A simple loop drawing is still required and an assessment of power/maximum surface temperature needs to be completed.

Conclusion

Flameproof (Ex d) offers hazardous area protection for zone 1 and 2 and offers protection for higher voltage (110 VAC, 220 VAC) applications and requires mechanical planning and preparation. For 24 V systems, intrinsic safety offers a simple and flexible solution for zones 0, 1 and 2. Intrinsic safety is the only protection that considers faults of the field wiring and offers live working without the need for a gas clearance certificate. It does require some design and planning to ensure that the system loop analysis is acceptable.

Note: Ex nL has been replaced by Ex ic for zone 2 in the standards. This means intrinsic safety can easily be used in zones 0, 1 and 2 and the wiring can be in the same multi-core cable or trunk. Another advantage of Ex ic is that the safety factor of 1,5 (as shown in Table A.2 of SANS/IEC 60079-11) does not need to be applied to cable parameters allowing for longer cable runs.

For further reading on using IS isolators in Functional Safety (SIL) Process Control loops, please see http://www.instrumentation.co.za/8903a

For more information contact Gary Friend, Extech Safety Systems, +27 (0)11 791 6000, gary@extech.co.za, www.extech.co.za

Credit(s)

 Tel: +27 11 791 6000 Fax: +27 11 792 8294 Email: sales@extech.co.za www: www.extech.co.za Articles: More information and articles about Extech Safety Systems

Preconfigured fail-safe circuit from Festo
Festo South Africa IS & Ex
The preconfigured Festo fail-safe circuit is ready to install in the control cabinet as a safe and low-cost alternative when it comes to fail-safe technology.

Flameproof cable glands
Pratley IS & Ex
A new flameproof cable gland range from Pratley allows for soft-bedding cables like PVC to be fitted to flameproof equipment without any concern regarding cable damage.

Eaton Oxalis CCTV cameras available from Extech
Extech Safety Systems News
Extech Safety Systems is pleased to announce that it has been appointed by Eaton to sell the Oxalis CCTV cameras in southern Africa.

Gigabit intrinsically safe Ethernet
Extech Safety Systems IS & Ex
Eaton’s 9470 product range provides cost-effective intrinsically safe (IS) Gigabit Ethernet equipment that can be installed and maintained easily in hazardous areas.

ifm - South Africa IS & Ex
With the new AL200S PROFIsafe IO-Link module from ifm electronic, it is now possible to operate standard safety sensors and actuators via IO-Link.

IS interface for signal processing
Endress+Hauser South Africa IS & Ex
Endress+Hauser’s RN series interface modules power the foundation of measurement instrument loops and safety instrumented systems.

Fluke’s intrinsically safe tools
Comtest IS & Ex
Fluke offers a growing number of intrinsically safe tools, which dampen the available energy at the output terminals and do not produce any static electricity.

Inventory management for LNG
Endress+Hauser South Africa IS & Ex
Endress+Hauser’s innovative instrumentation and advanced inventory management solutions for LNG storage tanks ensure safe operation of plant and high levels of inventory transparency.

Smart machines improve safety
Rockwell Automation IS & Ex
Manufacturers can harness the power of data to improve their safety compliance and performance using two new smart safety devices from Rockwell Automation.

Troubleshooting process loops in Ex areas
Comtest IS & Ex
Tracking down problems within a process loop can be a difficult challenge in the best of environments. Doing so in an area that has the potential for explosion takes the degree of difficulty to another level.