﻿ How to calculate an intrinsically safe loop approval - September 2017 - Extech Safety Systems - SA Instrumentation & Control

 classic | mobile

 Search...

How to calculate an intrinsically safe loop approval
September 2017, IS & Ex

We all know what can happen if the correct techniques are not used when interfacing into the hazardous area. Using intrinsic safety (Ex i based on IEC/SANS 60079-11; IEC/SANS 60079-25), the energy in the hazardous area is limited to below the ignition energy of the gas present, thereby preventing explosions.

For an explosion, all three of gas/dust, oxygen and source of ignition (spark or heat) need to be present. Intrinsic safety works on the principle of removing the source of ignition. This can be achieved by using a Zener barrier or galvanic isolator.

Zener barrier

A Zener barrier is a simple device where the voltage is limited by a Zener diode and the current by a resistor. A fuse is present to protect the Zener diode as shown in Figure 1. The key to safety is the intrinsically safe earth. Without it, there is no protection. If the input voltage increases above Zener diode voltage, the Zener conducts and the fuse blows, after which the Zener barrier needs to be replaced. In addition, the barrier has a volt drop across it under normal operating conditions, so careful calculation must be done to ensure that there is sufficient voltage at the field device. [Note: using Zener barriers without an IS earth is not safe.]

Figure 1.

Galvanic isolator

A galvanic isolator is an active device that energy limits without the dependence on the IS earth for safety as shown in Figure 2. It also has the advantage of supplying higher voltage at the hazardous area terminals and allowing longer cable lengths. Isolators have local LED indication and most 4-20 mA isolators transfer Hart communications through the optical isolation.

Figure 2.

Figure 3 defines Ex i for the various classifications of hazardous zones.

Figure 3.

Figure 4 shows that the barrier/isolator has [Ex ia] IIC; the square brackets indicate that the device (mounted in a safe area) can have connections to the hazardous area, in this case Ex ia i.e. zone 0 – IIC is the gas group. This transmitter has Ex ia IIC T4, which means it can be located in zone 0 in gas group IIC – T4 is the maximum surface temperature of the device (135°C).

Figure 4.

The barrier/isolator has maximum output parameters for voltage, current and power (Uo, Io and Po). These are maximum output values under fault conditions (known as safety description or entity parameters). The field device has maximum input parameters (Ui, Ii and Pi), which are the maximum values that can be applied under fault conditions and still be safe. [Note: for a safe loop all three input parameters must be greater than or equal to the corresponding output parameters.

To complete the system loop approval, the electrical energy stored in the cabling needs to be considered. Table A.2 in IEC/SANS 60079-11 lists the maximum cable capacitance against output voltage. In the example shown the maximum electrical stored energy that can be connected to the hazardous area terminals equates to Co = 83 nF and Lo = 4,2 mH. The transmitter has internal capacitance and inductance, so maximum cable capacitance Cc = Co-Ci and maximum inductance Lc = Lo-Li. The cable specification typically gives pF/m and μH/m allowing a calculation of maximum cable length

Based on this assessment, a system certificate or loop approval can be documented. [Note: inserting a barrier or isolator with a non-certified field device is not safe.] Some field devices (see Figure 5) like thermocouples are defined as Simple Apparatus.

Figure 5.

A simple loop drawing is still required and an assessment of power/maximum surface temperature needs to be completed.

Conclusion

Flameproof (Ex d) offers hazardous area protection for zone 1 and 2 and offers protection for higher voltage (110 VAC, 220 VAC) applications and requires mechanical planning and preparation. For 24 V systems, intrinsic safety offers a simple and flexible solution for zones 0, 1 and 2. Intrinsic safety is the only protection that considers faults of the field wiring and offers live working without the need for a gas clearance certificate. It does require some design and planning to ensure that the system loop analysis is acceptable.

Note: Ex nL has been replaced by Ex ic for zone 2 in the standards. This means intrinsic safety can easily be used in zones 0, 1 and 2 and the wiring can be in the same multi-core cable or trunk. Another advantage of Ex ic is that the safety factor of 1,5 (as shown in Table A.2 of SANS/IEC 60079-11) does not need to be applied to cable parameters allowing for longer cable runs.

For further reading on using IS isolators in Functional Safety (SIL) Process Control loops, please see http://www.instrumentation.co.za/8903a

For more information contact Gary Friend, Extech Safety Systems, +27 (0)11 791 6000, gary@extech.co.za, www.extech.co.za

 Credit(s) Supplied By: Extech Safety Systems Tel: +27 11 791 6000 Fax: +27 11 792 8294 Email: sales@extech.co.za www: www.extech.co.za
 Share: by email print

• PyroStorm provides cost-effective fire protection for control equipment
December 2018, Alien Systems & Technologies, IS & Ex
If you work at a large industrial plant or mine, you may have noticed those hydraulic lubricating oil packs, or perhaps the diesel generator sets, oil store rooms, pump rooms or flammable liquids stores, ...
• Compact safety light curtains for tight spaces
December 2018, RET Automation Controls, IS & Ex
The new SLC4 is Banner’s most compact safety light curtain to date. It has a low-profile design and a sensing area that extends the entire length of its 160 mm housing. This Type 4 safety light curtain ...
• Wise choices to decrease fire risk and improve safety
November 2018, Spero Sensors & Instrumentation, IS & Ex
Fire safety at the workplace is a topic that is easily neglected and many businesses do not devote enough attention to it. The topic quickly becomes top of mind when people lose their lives, or when a building or substantial part of an industrial plant is destroyed by fire.
• Network-based process visualisation
November 2018, Pepperl+Fuchs, IS & Ex
IT technologies such as PC and server virtualisation are establishing themselves in larger plants in the process industry to reduce the growing number of PC hardware components, while at the same time increasing flexibility and availability.
• PC-based control for the process industry
November 2018, Beckhoff Automation, IS & Ex
Beckhoff Automation adds Ex protection to extend its reach in hazardous areas.
• Don’t forget to test your fire protection systems before the holiday shutdown
November 2018, Alien Systems & Technologies, IS & Ex
As the year draws to a close, it is natural that people start looking forward to the holidays. It is therefore quite easy to neglect to consider the damaging effect a fire could have on businesses during ...
• Advanced light curtain improves safety
November 2018, Rockwell Automation, IS & Ex
The rise of robots has ushered in an increased demand for light curtains that provide a safe environment between the robotic work cells and the rest of the plant. The Allen-Bradley GuardShield 450L safety ...
• How to choose an industrial safety controller
September 2018, RET Automation Controls, IS & Ex
The following are five key features to look for in a safety controller that will save time and money, as well as help ensure that operators are using the safety system correctly. As with any safety application, ...
• Controllers simplify machines and improve safety
September 2018, Rockwell Automation, IS & Ex
The Allen-Bradley GuardLogix 5580 and Compact GuardLogix 5380 controllers from Rockwell Automation can be scaled from safety system levels SIL 2/PLd to SIL 3/PLe. This scalability can help engineers optimise ...
• Extech brings i.safe Mobile to sub-Saharan market-
September 2018, Extech Safety Systems, IS & Ex
Extech Safety Systems has partnered with GoRugged to distribute i.safe Mobile products in sub-Saharan Africa. The IS520.1 is an industrial smartphone with current technology for use in Zone 1/21. It combines ...
• Fire protection for unique risks
September 2018, Spero Sensors & Instrumentation, IS & Ex
Risk analysis is the first phase in choosing the best fire prevention solution for a company. Sperosens offers complete fire prevention solutions, tailored to the specific requirements of each customer. ...
• Using alarm annunciators in SIL-rated systems
September 2018, Omniflex Remote Monitoring Specialists, IS & Ex
In modern processing plants, the issue of functional safety is steadily gaining importance. Alarm annunciators are an integral part of safety planning, especially in processing plants where alarm conditions ...

 Contact: Technews Publishing (Pty) Ltd 1st Floor, Stabilitas House 265 Kent Ave, Randburg, 2194 South Africa Publications by Technews Dataweek Electronics & Communications Technology Electronic Buyers Guide (EBG) Hi-Tech Security Solutions Hi-Tech Security Business Directory Motion Control in Southern Africa Motion Control Buyers’ Guide (MCBG) South African Instrumentation & Control South African Instrumentation & Control Buyers’ Guide (IBG) Other Terms & conditions of use, including privacy policy PAIA Manual

classic | mobile